Setpoint. Display. Chromalox® Heil Quaker Boulevard • Lavergne, Tennessee Telephone: • FAX: QuickInfo. The Chromalox 1/4 DIN Temperature and Process Controller is a low cost, high performance single loop controller that can be used for temperature, flow. Find great deals for Chromalox rr RR Temperature Controller. Shop with confidence on eBay!.
|Published (Last):||17 November 2013|
|PDF File Size:||15.50 Mb|
|ePub File Size:||3.32 Mb|
|Price:||Free* [*Free Regsitration Required]|
1/4 DIN Temperature and Process Controller
On each PAGE you will find a specific set of related functions. To print the manual completely, chromalpx, download it. Operation cannot be reset until the process is out of the alarm condition.
The setpoint can be changed in the Normal Display Mode using the pushbuttons, if the Security Level allows setpoint changes see page 26 chromaoox Security Levels. The A typically ships in 1 working day or less plus allow additional time for your selected UPS or FedEx shipping method.
CHROMALOX TECHNICAL MANUAL Pdf Download.
Page 17 Figure 2. Page 11 When driving a contactor coil or other inductive load, an appropriately rated AC snubber circuit is recommended Chromalox Part. Page 59 The CLP is not a substitute for safety shutdown devices such as flow switches or overtemperature monitors.
Form C contact, 5A at or 2. The Digital Input can be setup to function as a remote alarm reset button see pages The program consists of 16 intervals plus a standby interval.
Value and the lower display shows the setpoint. Section 7 Digital Input and AUX Function The controller gives you two different options for actuation of any one of several field-selectable controller functions: The CLP Alarm responds to specific conditions that may provide early warning of system loop failures or aid in troubleshooting failures.
The sensor input of the can be calibrated using Sensor an appropriate sensor simulator and the Sensor Input Calibration menu on the Input Page.
Chromalox 2104-rr100 2104RR100 Temperature Controller
Seconds, Minutes, Hours 1 second to Getting Started With universal sensor inputs and front panel operator setup, one controller can be easily chromzlox configured for a wide variety of applications, and simply reconfigured as application needs change. Programmable for retransmission of Process Variable and Active Setpoint. Voltage Input Wiring Figure 2.
This organization allows you to go directly to the parameter to be adjusted, without stepping through a long series of unrelated entries. Page 63 Chromalox Technical Manual The DTR output is always enabled when the power is on. Wiring Terminal Identification Figure 2.
Dual Relay Output Wiring Wiring connections for the digital communications interface are made on terminals using shielded serial interface cable. Loop Alarm Output Output cchromalox, 4, or 5 will be activated if selected. Page 62 If a failure occurs in the control circuitry of the controller, the control output will be turned off and ERR3 will be displayed on the lower display.
| Temp and Process Controller | Chromalox – Valin
The control output will be turned off and the failure will be indicated by the lower display flashing LOOP. Enter text from picture: Input is setup for Auxiliary Setpoint. RS lines can be run over distances up to 50 feet.
Temperature extremes and excessive moisture can damage the instrument. Comments to this Manuals Your Name. Page 54 Operation cannot be reset until the process is out of the alarm condition. Digital Communications Hardware Setup RS can be used chromakox connect a computer or modem to a single controller.